- Do Not Drink Order Lifted
The city water sample came back clean. Tap water is ok to drink.
- Well #1 Repair – 7/12/22
The new pump failed with 5 sheared fins.
- Well Maintenance – 7/11/22
Well #1 has stopped producing water. The new pump and motor are still operating, but there is no flow.
Brian Cushman is coming out to pull the well on a warranty repair, and set the pump lower if needed.
- Well Maintenance – May, 2022
Bootster Pumps Before
Check-valve & Air-gap
- Well Maintenance Scheduled
Tuesday May 31st, 2022 @ 10:00am – 2:00pm
- Flow Meter Installation
- Booster Pump Check-valve Replacement
- Booster Pump Air-gap Replacement